Since 2000, Knight Heating and Air Conditioning, Inc. is your best choice for repair, installation, and service in homes and buildings just like yours in the 25 Mile Radius surrounding Otsego, MN. We take special pride in the craftsmen we train and employ--a fact you'll see in their reviews below. Its also noticeable immediately in the attitude and integrity our technicians bring to your job site. Our entire company works hard to make your experience with us hassle-free and enjoyable. You can also be assured that Knight Heating and Air stands behind the work we do as well as comply with all local codes. This is why, as you can see by the map and reviews below, we are rated so highly for Furnace and Air Conditioning Repair in Otsego, MN. Call us today at (763) 274-9945!
Knight did a great job on our furnace tune up. On time, friendly and knowledgable.
Installed new Trane high efficient furnace and Bradford white power vented water heater.
Installed new high efficient Trane xr16 air conditioner
Replaced capacitor on a goodman air conditioner and tested operation
Another Bryant capacitor
Real tough call, furnace switch was turned off accidentally, turned switch on and it works now!
Free estimate on a new furnace and air conditioner
Free Trane furnace and air conditioner estimate
Replaced capacitor on an icp condensing unit in otsego
Another blown capacitor this time on a luxaire air conditioner
Goodman air conditioner not working, found blown capacitor and fan motor shut down on hi limit. Replaced capacitor and cooled down the motor with water. Running good now
Removed bird from inducer motor on Lennox furnace
Found cracked heat exchanger in old Bryant furnace, installed new Trane 80% single stage furnace.
Rudd furnace not heating, cleaned flame sensor.
Emergency no heat call on luxaire furnace, found dirty flame sensor and cleaned it, tested operation.
Basement heat runs and returns
Carrier no heat
Installation of a new April aire 600 automatic humidifier
Heil no heat, replaced spark ignition module
Lennox air conditioner not cooling. Low on refrigerant, 410a charged system to proper temperature. Customer declined leak search
Goodman air conditioner not cooling, found compressor seized up, recommend replacing unit with Trane xr13 13 seer air conditioner.
Install basement ductwork
Gas leak at maxitrol regulator. Replaced regulator and cleaned and resealed leaking fittings. Re test for gas leaks, none found.